STUDER AND SOLAR MD
Studer and Solar MD Lithium-Ion battery has been tested with Xtender 48V models and allows for system capacities from 0.5kVA to 72kVA and up to 2MWh Lithium-Ion storage.
battery charger only
support to an AC source
== System overview ==
System overview Studer and Solar MD Lithium-Ion battery
The minimum required hardware for Studer + Solar MD system:
Minimum battery modules required and compatible models:
For SS237 – 25.6V (24V systems) please contact Solar MD support team for further assistance.
For the connection between LoggerV2 and Xcom-Can module. Only the Xcom-Can module must be connected to Logger V2, hence the VarioTrack / VarioString MPPTs and Xtender connect via private CAN to the Xcom-Can module.
Download: XCom-CAN manual, and read it carefully.
Arrange the DIP switches and Jumpers on the Xcom-CAN device as shown below:
Proceed to the Solar MD portal (http://login.mypower24.co.za)
Select Universal CAN Translator on CAN2.
Menu path: My Devices → Logger → Interfaces → CANBUS2.
After choosing Victron CAN Translator, proceed with Software reboot on the Logger V2 in the Tab “System Settings”.
Solar MD Logger V2 – Studer translator
Finally, the standard settings are 90% battery Depth of Discharge.
Contact our support team for further information.