GOODWE AND SOLAR MD
Goodwe ES Series range is a low voltage IP65 rated product, therefore a robust and safe product.
A good option for Hybrid Grid-connected systems.
== System overview ==
Wiring Schematics Goodwe ES and Solar MD
Minimum required hardware:
Use any UTP cable. Plug 2 of the wires (PIN 4, PIN 5) into the Solar MD Logger V2 CAN 2 connector. Plug the other side with RJ45 connector into the Goodwe ES BMS port:
Goodwe and solar MD wiring diagram BMS
The termination switch (120 Ohm) on Logger V2 should be on.
Digital control Configuration – CAN Bridge Software on LoggerV2
Firstly, on the Solar MD portal (http://login.mypower24.co.za) Select Victron Bridge on CAN 2:
CAN Bus bridge for Solar MD Logger V2
Menu path: My Devices → Logger → Interfaces →CANBUS 2.
Secondly, choose Victron Bridge, also proceed with Software reboot on the Logger V2 in the Tab “System Settings”.
For the Battery model choose Default 100Ah Lithium-Ion battery. Once all is correct you will see the following screen on EZ Manager:
GoodWe only accepts current values from the Logger V2 for maximum charge and discharge.